J. Bio. Env. Sci.5(5), 51-64, November 2014
The Biolac filtration system is based on active multi-stage sludge refineries. This system is a kind of modern biological methods in filtration of sewage waters and sludge’s which is so efficient in upgrading of lagoons. This survey aims at the investigation of qualitative sewage polluters and comparison of output results with Environmental Protection Agency (EPA) standards in Iran. First, after studying the details about this system, we focused on analysis of experimental results which was collected during the first six month range of 2010 to 2012 and performance evaluation of system linked to the removal ofBiochemical Oxygen Demand (BOD), Chemical Oxygen Demand (COD), Total Suspended Solids (TSS), N and P polluters. With regard to mentioned investigations and considerations, it can be concluded that the Biolac system was so successful in the removal of polluters such as BOD, COD and TSS. For BOD the average removal rates were more than 96 percent and the output value was less that 20 mg/lit. For COD the removal rates were more than 93 percent and the output value was less that 30 mg/lit. The average removal rate for TSS polluters was about 93 percent’s and the output value was less than 13 mg/lit. The corresponding rate for P polluters was about 72 and less than 3 mg/lit, respectively. We consider the EPA Standards in Iran and comparing the mentioned results with these standards, it will be evident that the effluent of such system can be discharged to surface waters.
Arumugam V. 1976. Recovery of chromium from spent chrome tan liquor by chemical precipitation. Indian Journal of EnvironmentalHealth.18, 47.
Bryant C, Wiseman C. 2003. Efforts to predict BOD for process control. In Proceedings.Tappi International Environment Conference.
Eckkenfelder W, Acevedo D, Babu S. 1965. Biological wastewater Treatmentplant .translated by Iwai . p 68 Korona.
Ekhaise F, Omavwoya B. 2008. Influence of Hospital Wastewater Discharged from University of Benin Teaching Hospital (UBTH). Benin City on its Receiving Environment. American-Eurasian Journal of Agriculture and Environmental Science. 4(4), 484-488.
Gary W, VanLoon S, Stephen J, Duffy M. 2012. Environmental Chemistry: A global perspective. Oxford Publisher.University Press. USA.
Ghomi MR. 2013. Environmental Report for Wastewater Treatment.Bazab Consulting Engineers. Urmia. Iran
Jafarpour M, Mehdipour AR, Nasehi A. 2013. reliability analysis of BIOLAC system in sewage treatment facility of Urmia city, third conference on programming and managing environment. Tehran. Iran.
Mackenzie D. 2010. Water and Wastewater Engineering.McGraw-HillPub.
MajlesiNasr M, YazdanbakhshA. 2008. Study waste sludge using hypochlorite and chlorine on wastewater treatment systems in hospitals of Iran. Journal ofEnvirontal Health Science Engineering. 5(3), 211-2115.
Mesdaghinia A, Khalegi A, Yazdankhah B. 2009. Wastewater Characteristics and Appropriate Method for Wastewater Management in the Hospitals. Iranian Journal ofWater and wastewater engineering .38 (1), 34-40.
Mir Bagheri A, Bazar R, Fathi M, Mosavi A. 2009. Evaluation of the Biolac Method in Municipal Wastewater Treatment. 2nd International Symposium of Environmental Engineering .Iran.
Mohammadi R, Rahimzade MH. 2013. Environmental Report for Wastewater Treatment Plant. Shafab Consulting Engineers.Urmia.Iran
Naeimi H, Mehrdadi N, Shahabi M. 2011. Evaluation of Refinery System based on Biolac Method and Presentation of Utilization Olan on Basis of ATV Standard (case study: Urmia Sewage Refinery Facility). 5th International Conference on Environmental Engineering. Tehran.Iran
Pathe P. 2005. Properties of chromium sludge chrome tan wastewater. Indian Journal of Environmental Protection. 15(2), 81-87.
Prakash NB. 2008. Bio-chemical treatment of tannery wastewater.Indian Journal of Environmental Protection. 22, 486-488
Sarafraz S, Khani MM, Yaghmaeian K. 2007. Quality and quantity survey of hospital wastewatersin Hormozgan province. Iranian Journal of Environmental HealthScience Engineering. 4(1), 43-50.
Standard Methods for the Examination of Water and Wastewater. 2006. Iranian Public Health Association, Tehran,Iran
Stenzel MH. 1993. Removal of Organics by activated carbon adsorption.Chemical Engineering Progress. 89 (4), 36-43.
Tchobanoglous G, Franklin L, Burton H, Stensel D. 2007. Wastewater Engineering: Treatment and Reuse. McGraw-Hill Science. Engineering. Math – 2002-03-26